How to repair the false fault of medical induction automatic door? Next Jinan induction automatic door to introduce you.
Pseudo fault 1: no matter whether people pass by or not, the medical induction automatic door keeps opening or closing.
1. It is possible that there are other moving objects in the sensing range of the detector. Check that other or animal bodies are removed around the automatic medical sensing door;
2. The detection range of the sensor may be adjusted too low. When the door is going to be closed, the probe and the sensor sense that the door senses activity, mistakenly believing that the moving object passes through, and the door is opened again;
3. It may be that the upper beam plate of the fixed induction probe is loose, which causes the probe to vibrate, so that the door leaf does not stop switching.
Pseudo fault 2: when the medical induction automatic door is loud in operation, most of such faults are due to the automatic door has been used for a long time.
1. After a long period of wear (a basic type of parts failure), the walking wheel of the door leaf spreader can be cleaned or a little lubricating oil can be added to the bearing of the walking wheel. However, it is not allowed to inject oil into the track and plastic walking wheel, because it is easy to absorb dust after oil injection, which makes the walking wheel damaged faster, such as equipped with The damaged parts shall be replaced and repaired in time;
2. Some metal connectors are loose, only need to be reinforced;
3. There is friction between movable door leaf and fixed door leaf, resulting in noise (DB);
4. The damage of the lower guide system will also cause loud sound;
5. The upper beam is not well done in the initial construction or has resonance with the ceiling.
False fault three: slow response of medical automatic induction door
1. The detection range of the induction probe is too small, so adjust the sensing range;
2. There is dust accumulation in the inner part of the induction probe, clean the dust;
3. The door body is too heavy, which exceeds the motor traction of the main engine.
Pseudo fault 4: the door leaf of the medical induction automatic door does not move, so you should see if you want to charge it.
1. Check whether the door leaves are pulled open. If this happens, the door will be very hard to start. The main controller will think there is an obstacle and carry out self-locking protection to stop the operation of the door;
2. Check whether the hoisting wheel of the door leaf falls off from the track. If this happens, the door leaf will also stop.
Note: only doing well in maintenance can reduce the incidence of false fault and improve the service life of medical induction automatic door.
The above is the analysis of induction automatic door fault. For more information, please click Jinan induction automatic door http://www.wshdgj.com Official website.